CAPACITY 755.81 Kw
Cooling capacity (Summer season operating conditions) 650,000 kcal / h
Cooling capacity (working condition in winter season) 1,300,000 kcal / h
HEAT TRANSFER SURFACE AREA 5.320 SQUARE METERS
AIR FLOW 470.000 Cubic Meters / H
AIR INTAKE TEMPERATURE 30 DEGREES
AIR OUTLET TEMPERATURE 35.8 DEGREES
25% ETHYLENE GLYCOL BLENDED
WATER FLOW 45 CUBIC METER HOURS
WATER INLET TEMPERATURE 50 DEGREES
WATER OUTLET TEMPERATURE 30 DEGREES
NUMBER OF FANS 10 PCS 800 MM
FAN Rossenberg – Germany
CONTROL BOARD Microprocessor control
Working principle: It is based on the principle of cooling the fluid passing through copper pipes supported by aluminum fins by sucking air with the help of fans.
CONTROL SYSTEM: It shows the operating temperature and the actual temperature, and the safe operation of the fans and water pumps is taken under control.